ARMY TM 9-6115-672-14
AIR FORCE TO 35C2-3-444-32
MARINE CORPS TM 09244A/09245A-14
d. Perform all AFTER (A) PMCS requirements in accordance with Table 2-5.
If software fails to boot properly, notify next higher level of maintenance.
e. Use keypad arrow buttons to move cursor to SHUTDOWN COMPUTER on CIM display screen. Use
SELECT button to click on EXIT button to exit the DCS software.
When CIM display screen displays message that it is safe to turn off the computer, place MASTER
CONTROL switch (12) in OFF position. Turn off panel lights.
g. Place DEAD CRANK switch (1) in OFF position.
PARALLEL UNIT OPERATION (LOAD SHARING).
Ensure generator sets are the same size and mode before attempting
2.12.1 General. The following method of parallel operation is used to share the load between two generator sets.
Refer to Figures 2-1 and 2-2 for location of operator controls and indicators mentioned below and Figure 2-
10 for proper paralleling configuration.
Prior to making any connections for parallel operation or moving a
generator set which has been operating in parallel, ensure there is no input
to the load output terminal board and the generator sets are shut down.
Failure to comply can cause injury or death to personnel by electrocution.
a. Ensure load requirement is equal or below the combined rated capacity of the two generator sets.
High voltage is produced when the generator set is in operation. Never
attempt to start the generator set unless it is properly grounded. Failure to
comply can cause injury or death to personnel.
b. Determine voltage requirements of load and position voltage reconnection terminal boards of the two
generator sets to the required voltage connection. Ensure FREQUENCY SELECT switches (10, Figure
2-8) on both generators are positioned for the same frequency requirements (50 Hz or 60 Hz).
c. Identify one generator set as No. 1 and the other as No. 2.
d. Open BATTERY ACCESS door (Figure 1-2).