ARMY TM 9-6115-672-14
AIR FORCE TO 35C2-3-444-32
MARINE CORPS TM 09244A/09245A-14
TABLE 2-1. DCS CONTROLS AND INDICATORS
CONTROL OR INDICATOR
ELAPSED TIME Meter
Indicates total engine operating hours.
Illuminate DCS control panel.
EMERGENCY STOP Switch
Shuts down generator set when activated. Removes electrical
power to governor controller and stops engine from operating.
PANEL LIGHTS Switch
Activates and deactivates panel lights.
NETWORK FAILURE Indicator
When illuminated indicates a failure between Computer
Interface Module and Input/Output Module. Generator set will
not continue to operate, and capability to monitor its operation
and to make adjustments will be degraded or lost.
BATTLE SHORT Switch
Bypasses protective devices on generator set. Set will continue
to operate until overvoltage occurs or fuel is exhausted.
ETHER START Switch
When held in ON position momentarily during engine cranking,
activates ether cold weather starting system for starting engine
at temperatures below 40°F (4°C).
ENGINE CONTROL Switch
Four position switch:
OFF de-energizes all circuits except panel lights and power to
PRIME & RUN AUX FUEL energizes generator set run
circuits with auxiliary fuel pump operating.
PRIME & RUN energizes generator set run circuits with
auxiliary fuel pump de-energized.
START energizes engine starter and flashes generator field.
FREQUENCY ADJUST Switch
Momentary-action toggle switch. Adjusts frequency output of
generator set for each activation of the switch. Works in both
directions to increase and decrease output frequency.
AC CIRCUIT INTERRUPT Switch
Opens and closes AC Circuit Interrupt Relay. Used during
VOLTAGE ADJUST Switch
Momentary-action toggle switch. Adjusts voltage output of
generator set. Works in both directions to increase and
decrease output voltage.
FAULT RESET Switch
Resets (turns off) fault indicators displayed on Computer
Interface Module display screen. Will re-energize governor
MASTER CONTROL Switch
When placed in ON position, provides battery power to DCS.
Should be first switch activated on panel. Generator set cannot
be started unless switch is activated.
GROUND FAULT CIRCUIT
INTERRUPTER TEST Switch
Tests GROUND FAULT CIRCUIT INTERRUPTER.
GROUND FAULT CIRCUIT
INTERRUPTER RESET Switch
Resets GROUND FAULT CIRCUIT INTERRUPTER.
Keypad Up Arrow Pushbutton
Moves cursor on CIM display screen in upward direction until
Keypad Right Arrow Pushbutton
Moves cursor on CIM display screen to the right until released.
Keypad SELECT Pushbutton
When pressed, selects item on CIM display screen indicated by
Keypad Down Arrow Pushbutton
Moves cursor on CIM display screen in downward direction