ARMY TM 9-6115-672-14
AIR FORCE TO 35C2-3-444-32
MARINE CORPS TM 09244A/09245A-14
DC voltages are present at generator set electrical components even with
generator shut down. Avoid shorting any positive terminal with
ground/negative. Failure to comply can cause injury to personnel and damage
Open BATTERY ACCESS door (Figure 1-2), and disconnect negative battery cable.
Open left side engine compartment access doors (Figure 1-2).
Tag and disconnect electrical leads from either solenoid valve (3, Figure 4-27).
Disconnect tube assembly (10) from adapter (19) and spray nozzle (11).
Loosen wingnut (1), and unscrew ether cylinder (2) from ether solenoid valve (3).
Install cap (4) on ether solenoid valve (3).
Remove nuts (12), lockwashers (13), washers (14), relay (16), and bolts (15) from generator set
Remove bolts (17) from bracket (18) and remove solenoid (3) from bracket.
(10) Remove adapter (19) from solenoid (3).
(11) Remove spray nozzle (11) from engine intake manifold.
(12) Close engine compartment doors.
Remove ether solenoid valve, step a above.
Inspect ether solenoid valve (3, Figure 4-27) for cracks, corrosion, damaged threads, and other
Inspect tube assembly (10) for cracks, breaks, pinching, damaged threads, and other damage.
Inspect spray nozzle (11) for cracks, corrosion, clogging, and other damage.
Replace any defective parts.
Install ether solenoid valve, step c below.