4.16 POWER DISTRIBUTION UNIT CONNECTION PANEL MAINTENANCE.
This task covers:
General Mechanics Tool Kit
(item 2, appendix B)
Automotive Fuel and Electrical System Repair, Tool
Kit (item 3, appendix B)
Shut down Generator Set
150 kW, paragraph 2.8.1.
Never attempt to disconnect control or power cables while the
Generator Set 150 kW is running. Failure to observe this
warning could result in severe personal injury or death by
a Disconnect control cable:
(1) Unscrew protective cap (4, Figure 4-19) for plug and protective cap (3) for socket from
(2) Pull plug of control cable (1) out of socket (2).
(3) Screw protective cap (4) onto plug of control cable (1).
(4) Screw protective cap (3) onto socket (2).
Disconnect power cables (5,6,7,8) using the same procedure as for the control cable.
If U. S. Standard Grounding Assembly is used for grounding,
disconnect grounding cable (27) from grounding connector (26).
If grounding cables are attached on grounding bar (25) do steps c.
Remove nut (10), serratad lock washer (11), washer (12) and grounding cable (13) from grounding
stud (14). Put washer (12) and serrated lock washer (11) back on, and screw nut (10) on