Table 3-2. Operator Preventive Maintenance Checks and Services (Cont).
Item To Be Inspected,
Equipment Is Not
Procedure: Check For And Have
Repaired, Filled, or Adjusted As Needed
GENERATOR SET GAGES AND INSTRUMENTS
i. Check that all lights on fault indicator panel (42) Fault light will not go out
are out during operation. Check bulb operation when switch is set to TEST
with TEST or RESET switch on panel.
or RESET position, then
released. All bulbs should
be lit when switch is in TEST
or RESET position.
Do not smoke or use open flame in vicinity of
power unit while refueling generator set.
a. Fill set tank and auxiliary tank upon completion
Fuel system temperature must be above
freezing when draining water and sediment.