ARMY TM 9-6115-644-24
AIR FORCE TO 35C2-3-446-12
MARINE CORPS TM 09249A/09246A-24/2
In an NBC contaminated environment, the generator set should be operated with all access doors closed to re-
duce the effects of contamination.
The use of overhead shelters or chemical protective covers is recommended as an additional means of protec-
tion against contamination in accordance with FM 3-5. When using covers, care should be taken to provide adequate
space for air flow and exhaust.
For additional NBC information refer to FM 3-3 and 3-4. Other services use applicable publications for NBC.
S e c t i o n V l l l . M A I N T E N A N C E O F D C E L E C T R I C A L S Y S T E M
This section contains unit maintenance procedures for the DC
inspection/repair which are beyond the scope of unit maintenance
Deficiencies noted during
shall be reported to the next higher level of
Refer to TM 9-6115-644-10 for all operator procedures
2-11 BATTERY AND SLAVE RECEPTACLE CABLES.
Batteries give off a flammable gas. Do not smoke or use open flame when performing
maintenance. Flames and explosion could result in severe personal injury or death.
Remove metal jewelry when working on electrical system or components. Failure to ob-
serve this warning could result in severe personal injury or death by electrocution.
This procedure is typical for the positive, negative, and interconnect battery cables,
and the positive and negative NATO slave receptacle cables.
Shut down generator set.
Open battery access door and right side engine access doors.
Inspect battery/slave receptacle cables for security; cracked insulation; broken, burned or corroded terminals;
missing parts; or other damage.
Close access doors.