ARMY TM 9-6115-644-24
AIR FORCE TO 35C2-3-446-12
MARINE CORPS TM 09249A/09246A-24/2
Make sure all disc mounting holes at the inner and outer diameters are properly
Ensure correct positioning of spacers (19), washers (18), and bolts (17) as marked
Install drive discs (22) on drive hub (26) with spacers (19), washers (18) and (21), and bolts (17) and (20). Torque
bolts (20) to 28 ft-lbs (38 Nm) and bolts (17) to 35 ft-lbs (47 Nm)
Install generator assembly in generator set, paragraph 4-17-2.
4-24 GENERATOR MAIN STATOR AND HOUSING.
Shut down generator set. Allow generator to cool to ambient temperature.
Open battery access door and disconnect negative battery cable.
Remove protective cover and moveable terminal board from voltage reconnection terminal board,
Disconnect two electrical connectors from bottom of control box assembly.
Tag and disconnect wires 107C and 109J from terminals 1 and 2 of power potential transformer
(37, FIGURE 4-5).
Connect resistance bridge and note readings between terminals T1 and T4, T2 and T5, T3 and T6, T7 and T0,
T8 and T0, and T9 and T0 of AC voltage reconnection terminal board.
All resistance readings should be as shown in TABLE 4-3.
If resistance is low, there are shorted windings, if resistance is high, stator windings are open. In either case,
stator must be replaced.
Disconnect removable grounding link on load output terminal board (17, FIGURE 2-29).
Set multimeter for ohms and connect between each coil lead and ground, in turn.
If multimeter indicates resistance on any connection, stator windings are grounded and stator must be replaced.
Connect removable grounding link on load output terminal board.
Connect wires 107C and 109J to terminals 1 and 2 of power potential transformer. Remove tags.
Connect two electrical connectors to bottom of control box assembly.
Install moveable terminal board and protective cover on voltage reconnection terminal board, paragraph 2-96-3.
Connect negative battery cable and close battery access door.