ARMY TM 9-6115-644-24
AIR FORCE TO 35C2-3-446-12
MARINE CORPS TM 09249A/09246A-24/2
Remove load measuring unit, paragraph 2-65-2.
b. Install new Ioad measuring unit, paragraph 2-65-3.
Section Il. MAINTENANCE OF COOLANT SYSTEM
Repair radiator in accordance with TM 750-254.
Section Ill. MAINTENANCE OF FUEL SYSTEM
a. Shut down generator set.
b. Remove fuel tank, paragraph 4-7-2.
Inspect fuel tank (6, FIGURE 4-4) for leaks, cracks, missing hardware, and other damage.
d. If no damage is found, install fuel tank, paragraph 4-7-3.
a. Shutdown generator set.
b. Open battery access door and disconnect negative battery cable.
Diesel fuel inflammable and toxic to eyes, skin, and respiratory tract. Skin/eye protection
required. Avoid repeated/prolonged contact. Good general ventilation is normally ade-
Drain fuel tank
d. Remove engine and generator assembly, paragraph 3-6-1.
Remove fuel tank drain valve, paragraph 2-69-1.
Remove nuts (1, FIGURE 4-4), Iockwashers (2), washers (3), bolts (4) and plates (5) securing fuel tank to skid
Remove fuel tank (6) from skid base.
h. Remove low fuel level/ auxiliary fuel pump float switch, paragraph 2-91-2.
Remove fuel level sender, paragraph 2-90-2.