ARMY TM 9-6115-644-24
AIR FORCE TO 35C2-3-446-12
MARINE CORPS TM 09249A/09246A-24/2
h. Connect negative battery cable. Close battery access door.
2-68 CONTROL PANEL FRAME.
Shut down generator set.
Open battery access door and disconnect negative battery cable.
Remove control box assembly, paragraph 2-19-2.
Remove control panel, paragraph 2-67-1.
Remove diagnostic connector, paragraph 2-63-2 (do not remove wires).
Remove parallel connector, paragraph 2-64-2 (do not remove wires).
Remove CONVENIENCE RECEPTACLE, paragraph 2-46-3; GROUND FAULT CIRCUIT INTERRUPTER,
paraqraph 2-47-3; and malfunction indicator panel, paragraph 2-48-3.
Remove bolts (14 and 16, FIGURE 2-19), nuts (15) and (17), damp (18), and control panel frame (19) from con-
trol box assembly.
If necessary, drill out rivets (20), (22), and (24) and remove identification plates (21), (23), and (25).
Inspect control panel frame (19, FIGURE 2-19) for dents, cracks, loose paint, and corrosion.
Wear a protective mask and gloves when sanding CARC painted surfaces. CARC paint
dust is a health hazard and could cause personal injury if warming is not followed.
Repair all dents and cracks, and remove all loose paint.
Remove light corrosion with fine grit abrasive paper (Item 16, Appendix C).
Repaint surface in accordance with TM 434139. (F) Refer to applicable directives.
Install control panel frame (19, FIGURE 2-19) and damp (18) to control box assembly with bolts (14) and (16)
and nuts (15) and (17).
If removed, install identification plates (21), (23), and (25) on control panel frame (19) with rivets (20), (22), and
Install malfunction indicator panel, paragraph 2-48-4; GROUND FAULT CIRCUIT INTERRUPTER, paragraph
2-47-4; CONVENIENCE RECEPTACLE, paragraph 2-46-4; parallel connector, paragraph 2-64-3; and diagnos-
tic connector, Paragraph 2-63-3.
Install control panel, paragraph 2-67-4.
Install control box assembly, paragraph 2-19-4.
Connect negative battery cable and dose battery access door.