Depressing the EMERGENCY STOP pushbutton
will stop the generator set.
The generator set cannot be restarted
without resetting the EMERGENCY
STOP pushbutton and turning MASTER
SWITCH to OFF position.
OPERATION USING BATTLE SHORT
Continued operation using the BATTLE
SHORT switch can result in damage to
the generator set.
If any emergency situation requires
continued operation of the generator set,
the BATTLE SHORT switch is used to
override all protection devices except
rhe overspeed, short circuit devices, and
EMERGENCY STOP function.
BATTLE SHORT switch must be OFF
to start generator set.
Start generator set, if set is not running.
Refer to paragraph 2-9.1.
b. Lift cover on BATTLE SHORT switch
and position switch to ON.
If the OVERSPEED light on the
illuminated, position the AC circuit
interrupter to the OPEN position until
indicator goes out on each set.
ARMY TM 9-6115-644-10
AIR FORCE TO 35C2-3-446-11
MARINE CORPS TM 09249A/09246A-10/1
2-22 OPERATION WHILE CONTAM-
The generator set will operate in a normal manner
when exposed to nuclear, biological or chemical
(NBC) contamination. It is capable of being
operated by personnel wearing NBC clothing
without special tools or support equipment. Refer
to FM 3-3, FM 3-4, and FM 3-5.
USE OF THE CONVENIENCE
Power is available when the main
contactor is open. Avoid accidental
Failure to observe this
warning can result in severe personal
injury or death by electrocution.
The maximum power rating for the
convenience receptacle is 10 Amps.
Continuous operation above 10 Amps
can result in damage to the generator
a. Start the generator set if it is not
operating. Refer to paragraph 2-9.
b. Ensure the load does not exceed the
c. Reset the Ground Fault Circuit
Change 2 2-39/(2-40 blank)