Never attempt to start the generator set if it is
not properly grounded. Failure to observe this
warning could result in serious injury or death
b. Determine voltage requirements of load and posi-
tion voltage reconnection terminal boards of the two
generator sets to the required voltage connection.
E n s u r e F R E Q U E N C Y S E L E C T s w i t ch
(MEP805A) for both generators are positioned for
the same load requirements.
c. Identify one generator set as No. 1 and the other as
d. Remove paralleling cable from storage box located
inside battery compartment access door.
ARMY TM 9-6115-644-10
AIR FORCE TO 35C2-3-446-11
MARINE CORPS TM 09249A/09246A-10/1
e. Connect the paralleling cable between the two gen-
erator sets. Connect the generator sets to the load
observing the proper phase polarity.
Do not close the AC CIRCUIT INTERRUPT-
ER switch on either of the generator sets, nor
close the load contactor at load until specifical-
ly directed to do so. Closing any of these de-
vices at any other time may severely damage
one or both of the generator sets.
a. Start each generator set, refer to paragraph 2-9.1.
b. Rotate both VOLTAGE adjust potentiometers to ob-
tain the same voltage indication on each set.
Change 1 2-25