ARMY TM 9-6115-442-10
AIR FORCE TO 35C2-3-455-11
MARINE CORPS TM 09247A/09248A-10/1
Perform all before (B) PMCS, refer to TABLE 2-4.
Place DEAD CRANK SWITCH in NORMAL position.
Push DC CONTROL POWER circuit breaker m.
Ensure AC voltage reconnection switch is positioned
to match voltage requirements.
Place AM-VM transfer switch in a position
corresponding to output terminal load connections,
refer to TABLE 2-1.
Pull our EMERGENCY STOP switch.
Place MASTER SWITCH to PRIME AND RUN
Push PRESS TO TEST pushbutton on malfunction
indicator panel. Ensure all indicator lights are lit.
When PRESS TO TEST pushbutton is released, all
lights should go out.
Press BATTLE SHORT press to test light on the
control panel assembly. Ensure indication light is lit.
When press to test light is released, light should go
Press AC CIRCUIT INTERRUPTER press to test
light on the control panel assembly. Ensure indicator
light is lit. When press to test light is released, light
should go out.
High voltage is produced when generator set is in
Operation. Improper operation could result in
personal injury or a death by electrocution.
2-20 Change 1