ARMY TM 9-6115-641-24
AIR FORCE TO 35C2-3-456-12
UNIT MAINTENANCE INSTRUCTIONS
Section I. SERVICE UPON RECEIPT OF EQUIPMENT
INSPECTING AND SERVICING THE EQUIPMENT.
This section provides information and guidance for inspecting, servicing, and installing the generator set under normal
Unpack and inventory all end item components for serviceability.
Check that all packing materials have been removed.
Check generator set identification plate for positive identification.
Inspect generator set for any internal or exterior shipping damage.
Open engine compartment access doors and inspect batteries for damage.
Check battery cables for damage.
Open control panel access door and check panel for damage.
Lower control panel and check electrical connections for damage or loose connections.
Check air cleaner assembly and exhaust opening for obstruction.
Check fan drive belt for proper adjustment, paragraph 2-75-4.
Inspect generator set for loose or missing mounting hardware or damaged or missing parts.
Check oil level. Ensure that oil level is at FULL mark on dipstick If required, add engine lube oil specified in
Unpack grounding rod, and auxiliary fuel hose. Inspect each item for damage.
For Battery service refer to TM9-6140-200-14
Do not operate generator set while servicing radiator. Damage to equipment or
personal injuries may result.
a. Remove radiator cap
b. Check that radiator drain valve (Figure 1-12) is closed.