ARMY TM 9-6115-641-24
AIR FORCE TO 35C2-3-456-12
Remove voltage reconnection switch, paragraph 2-64-2.
Set multimeter for ohms and check voltage reconnection switch for continuity. Refer to Electrical Schematic
FO-1 (S-8 Circuit Schedule) to determine switch circuits made to corresponding switch positions.
Check continuity of switch circuits in all three switch positions.
If open circuit is indicated in any switch position, voltage reconnection switch is defective and must be replaced.
If replacement is not required, install voltage reconnection switch, paragraph 2-64-4.
Install mounting bracket (16, Figure 2-16) with screws (15) in output box assembly.
When installing the voltage reconnection switch, use extreme care not to drop
the attaching hardware down on the generator unit. Serious damage to the equip-
ment could result.
Install voltage reconnection switch (14) in output box assembly and secure with screws (9) and (12), washers
(10), and nuts (11) and (13).
Connect electrical leads to voltage reconnection switch as tagged and remove tags.
Install control box assembly, paragraph 2-16-4.
Connect negative battery cable and close access door.
Section XII. MAINTENANCE OF AIR INTAKE AND EXHAUST SYSTEM
Shut down generator set.
Open both engine access doors and disconnect negative battery cable.
The exhaust system can get very hot. Allow system to cool before performing
maintenance. Failure to follow these instructions could result in severe burns
Remove bolts (1, Figure 2-18) and Iockwashers (2) at intake manifold.
Remove bolts (3), lockwashers (4), muffler (5), exhaust seal (6), retaining plate (7), and exhaust seal spring
(8) from generator set.
Remove gasket (9) from exhaust manifold.
Unlace safety wire (10) and remove wrap (11) from muffler (5).