ARMY TM 9-6115-641-24
AIR FORCE TO 35C2-3-456-12
a. Shut down generator set.
b. Open left side engine access door and disconnect negative battery cable.
Release control panel by turning two fasteners and lower control panel slowly.
d. Tag and disconnect panel light (3, Figure 2-14) electrical leads.
Remove nut (1) and washer (2).
Remove panel light (3) from control panel.
Remove panel light directional cap (4, Figure 2-14) from panel light housing (3).
Remove panel light bulb (5).
Install panel light bulb (5, Figure 2-14) into panel light housing (3).
Install panel light directional cap (4).
Insert panel light (3, Figure 2-14) into control panel.
b. Install washer (2) and nut (1).
Connect panel light electrical leads and remove tags.
Raise and secure control panel.
Connect negative battery cable and close access door.
2-38. PRESS TO TEST INDICATOR LIGHTS.
Inspect indicator lights for cracks, corrosion, evidence of shorting, and other damage.
Replace or repair indicator lights or components as necessary.
Place MASTER SWITCH in either PRIME & RUN position.
Press in lamp holder (6, Figure 2-14) and check that lamp is lit.
If lamp (7) fails to light, set multimeter for DC volts and check for battery voltage at receptacle (10) terminals
1 and 3.
If voltage is present, replace press to test light assembly.