Table 32. Operator/Crew Preventive Maintenance Checks and Services (PMCS) - Cont.
D A W
Item to be Inspected.
Procedure: check for and
have repaired, filled, or
adjusted as needed
Perform weekly as well as before PMCS if
you are operating the equipment for the first
GENERATOR SET EXTERIOR
Slight fuel leak (Class I or II leaks) by the
control unit shaft is normal and is necessary
to lubricate shaft. Any other fuel leak or
fuel leakage around the control unit shaft is
a Class III leak and makes the equipment
a. Check on, around, and beneath the
generator set (1) for fuel or oil leaks.
b. Check that generator set (1) grounds are
properly installed, and grounding
connections are tight.
Check fuel gage (2) for sufficient fuel for
Equipment is Not Ready/
A Class III lubrication oil or
any class fuel leak is detected.
Not properly grounded.