Section IV. TROUBLESHOOTING
Power Unit Troubleshooting. There are no troubleshooting procedures authorized at operator
level for the power plant end item. Troubleshooting procedures for the individual generator sets and
trailers are contained in their respective technical manuals referenced below.
a. Generator Set Troubleshooting. Refer to TM 5-6115-545-12 for troubleshooting procedures
applicable to the generator set.
b. Trailer Troubleshooting. Refer to TM 9-2330-205-14&P for troubleshooting procedures
applicable to the trailer.
Section V. OPERATOR/CREW MAINTENANCE
Fire Extinguisher Maintenance. The AN/MJQ-12A Power Plant is equipped with two 5 lb C02
fire extinguishers. Maintenance is limited to weighing the fire extinguishers monthly to insure that they
are sufficiently charged. Fully charged, each fire extinguisher weighs 13 lbs. Send the unit to
specialized activity for recharging if it weighs 12.5 lb or less.
Do not attempt to verify readiness of a fire extinguisher by partially discharging
unit. Any discharge of contents will require refilling.