Table 3-2. Operator/Crew Preventive Maintenance Checks and Services (PMCS) CONT.
B - Before
D - During
A - After
W - Weekly
M - Monthly
Inspect and weigh fire extinguisher.
(See paragraph 3-11.)
Inspect entire chassis frame for damage,
Frame is obviously broken
cracks, and broken welds.
Check level of fluid in cooling system.
Proper level is 2 inches below overflow
pipe. Add coolant as required.
Section IV. TROUBLESHOOTING
3-10. Power Plant Troubleshooting. There are no troubleshooting procedures authorized at operator level
for the power plant end item.
Troubleshooting procedures for the individual generator sets and trailers
are contained in their respective technical manuals referenced below.
Generator Set Troubleshooting.
Refer to TM 5-6115-464-12 for, troubleshooting procedures
applicable to the generator set.
Trailer Troubleshooting. Refer
to the trailer.
Fire Extinguisher Maintenance.
Maintenance is limited
to TM 9-2330-205-14&P for troubleshooting procedures applicable
The AN/MJQ-15 Power Plant is equipped with two 5 lb C02 fire
to weighing the fire extinguishers monthly to insure that they are
sufficiently charged. Fully charged, each extinguisher weighs 13 Ibs.
Send the unit to specialized
activity for recharging if it weighs 12.5 lb or less.
Do not attempt to verify readiness of a fire extinguisher by partially
discharging unit. Any discharge of contents will require refilling.