Using slide hammer, remove ground rod. Disassemble, clean, and stow ground rod in
Disconnect power unit from external fuel source, if applicable.
Stow any remaining authorized equipment in accessory box.
Secure fire extinguisher and fuel cans in their respective mounting brackets.
Close all doors on the generator set enclosure.
Swing personnel platform up into traveling position and secure with two platform anchor quick-
W A R N I N G
Use care when releasing spring-loaded lower tube of leveling jacks. The lower
tube will return to retracted position with considerable force and can cause
Retract lower tubes of leveling jacks. Swing leveling jacks up into traveling position and secure
Remove wheel chocks.
Attach power unit to towing vehicle. Refer to TM 9-2330-205-14&P.
Release trailer handbrakes.
4-4. Reinstallation After Movement. After movement to a new worksite, install power unit in
accordance with paragraph 4-2.
Section III. REPAIR PARTS, SPECIAL TOOLS, SPECIAL TEST, MEASUREMENT AND
DIAGNOSTIC EQUIPMENT (TMDE)
4-5. Tools and Equipment. There are no special tools or equipment required to maintain the
PU 405A/M power unit.
4-6. Maintenance Repair Parts. Repair parts and equipment for maintenance of this power unit are
listed and illustrated in the repair parts and special tools list in Appendix D of this manual.
Section IV. LUBRICATION INSTRUCTIONS
4-7. G e n e r a l . Detailed instructions for the lubrication of the major components of the power unit
are contained in the applicable Lubrication Orders (LOs). Refer to DA Pam 310-1 to ensure that the
latest editions of the L.O.S are used. This section contains lubrication instructions that are not
included in the Lubrication Orders.
4-6. Generator Lubrication. Refer to TM 5-6115-464-12 for generator set Lubrication Order.
a. Trailer Lubrication. Refer to TM 9-2330-205-14&P fort tailer Lubrication Order.