HEATER ATTACHMENT MAINTENANCE.
This task covers:
Tool Kit, General Mechanic's
Generator shut down, TM 9-6115-642-10
Disconnect negative battery cable from right battery and the
positive battery cable from the left battery before doing the
following procedures. Failure to observe this warning could
result in severe personal injury or death.
Keep spilled fuel away from hot engine and all fires, and wash
with warm water after getting any on skin. Fuel is highly
flammable and is irritating to skin.
Turn Heater and generator off.
2. Open left and right access doors and disconnect negative battery cable from right battery and positive battery cable
from the left battery.
3. Support heater. Remove screws (1, 3, 4, Figure 4-23), washers (2, 7, and 8), nut (11), lockwashers (5, 6, and 9) and
heater from heater mounting brace (10), and heater mounting brace (10) from wall mounting bracket (12) and wall mounting
Inspect all hardware (1-13) for damage and replace as required.
Install wall mounting bracket (12) with screws (4), lockwashers (6) and washers (8) to generator housing (14).
Install heater to heater mounting brace (10) with screws (1), washers (2), lockwashers (9) and nut (11).
Install heater mounting brace (10) to wall mounting bracket (12) with screws (3), lockwashers (5), and washers (7).
Reconnect batteries and close access doors.